How to treat a ever-tripping circuit breaker?
Circuit breaker question: I have a 20 amp breaker that keeps tripping. Can I replace it with a stronger one? Or...?
How to get rid of mice?
We seem to have some unwelcome Mickeys and Minnies in our house. What is the best way to get rid of them?
How to remove popcorn ceiling with asbestos?
I want to remove my popcorn ceiling, but it has asbestos in it. How do I go about this safely?
How to trap fruit flies?
Does anyone know how to get rid of fruit flies with a homemade trap?
How to remove popcorn ceiling with vacuum?
Is there a way to use a vacuum to remove a popcorn ceiling?
How to fix a crack in a door frame?
How to fix a door frame with a split in it?
How do I kill the power from my main breaker?
I have a home built in 2006, the main panel does not seem to have a main breaker...? See attached pic of the main panel. It's a Siemens G3040 200 amp panel. Outs... See more
Any Ideas for this corner with the wood stove pipe?
I am unclear as to what to do with this part of my house, "The Breakfast Nook".
There is a reason that the breaker keeps tripping. You need to figure that out first! Something is wrong somewhere. The breaker tripping is a safety feature.
Gk is so right-you will have to test various areas to find the 'culprit'-something in an area is causing the trip so get a friend to be near breaker box and you 'off-on' electrical items -anything you 'plug in'
The most common cause of a circuit breaker tripping is an overloaded circuit...too many things plugged into one circuit. To correct this issue you’ll need to unplug something on that circuit. Definitely do not put in a larger amperage breaker as this can cause a fire.
Something on that breaker is tripping it by using more amps in addition to the other things on the breaker. Is there something that you added just before the breaker getting tripped? Hubby is an electromechanical engineer by education. He says that about 15 years is the max life for a breaker, it is possible that it needs to be replaced. 20 amps is already a heavy duty breaker and you can't go higher because of the makeup of the wiring that will take only so many amps without overheating the wires and causing a safety issue. Either the circuit breaker is old and weak, or you are drawing too many amps for the breaker by adding something that requires more amperage than is available with what was already using the breaker, like adding a high draw item like a deep fat fryer.
Here is a decent place to find a suitable circuit breaker, also pay attention to the curve type or class such as A, B,C, D. B and C are usually for residential applications.