Why does my WH pilot go out when the wind blows outside?
Why does my WH pilot go out when the wind blows outside New water heater and already replaced roof ventwaterheater is in basement thx
How to get rid of mice?
We seem to have some unwelcome Mickeys and Minnies in our house. What is the best way to get rid of them?
How to remove popcorn ceiling with asbestos?
I want to remove my popcorn ceiling, but it has asbestos in it. How do I go about this safely?
How to remove popcorn ceiling with vacuum?
Is there a way to use a vacuum to remove a popcorn ceiling?
How to trap fruit flies?
Does anyone know how to get rid of fruit flies with a homemade trap?
How to fix a crack in a door frame?
How to fix a door frame with a split in it?
How do I kill the power from my main breaker?
I have a home built in 2006, the main panel does not seem to have a main breaker...? See attached pic of the main panel. It's a Siemens G3040 200 amp panel. Outs... See more
Any Ideas for this corner with the wood stove pipe?
I am unclear as to what to do with this part of my house, "The Breakfast Nook".
is vent covered/hooded ? still getting 'blow back' from somewhere ... call your plumber ...
If it is a new water heater contact the manufacturer and explain this to them. They should be able to give some precise info.
Is the vent termination on the roof substantially higher than any nearby roof? If it is too low, the roof may be having an effect on venting. Try spending time near your heater when it's windy. Can you feel any drafts around the heater; top or bottom? If so, try to position things to protect the base of the heater from the drafts. If there are drafts coming down the vent, a taller vent and possibly better style vent cap could help. Make sure both inner and outer combustion chamber doors are in place. Is the pilot light quite small? Very small pilots are easier to blow out and could indicate a partly clogged pilot orifice. Does the pilot flame hit the end of the thermocouple nicely? Tightly insulated homes can be a vaccuum on windy days. The wind sucks air out of the inside an tight home and airs moves through the path of least resistance, the heater vent. The pilot flame can actually be pulled off the pilot assembly and blow out.
Sounds like either you have blowback or the flame is being drawn out by a vacuum effect.